The attached instructional video shows how to configure the IP address of a Wago module via the Sectormaster software.
The most critical steps of the process are:
1. Within Windows Firewall, create new Inbound and Outbound rule for ports 67, 68
2. Select the BootP option in the software configuration envir
3. Cycle power to the scanner before activating the software runtime environment so that scanner can be ready to acquire the Wago module IP address from the software via the BootP server.