Q. The analog output signal does not match the calculated sector or zone values, or the control system reading does not match the calculated sector or zone values.
A. Check that the PLC input scaling matches the output scaling in the DTDP configuration. Alternatively, check that each Wago analog output card is set appropriately (should be 4-20mA) but could be set to 0-20mA. Wago 750-563 analog output modules are configurable for 0-20mA or 4-20mA and should have been set at the factory (if the customer purchased from us). https://fluke.freshdesk.com/en/support/solutions/articles/19000122156-faq
Q. In Zonemaster, how to do I connect the trigger input
A. On the X3 DIN terminal rail, connect you trigger signal (5-24V) to pins 13 (red for +ve ) and 14 (pink for -ve).
Q. On the X3 DIN terminal rail, I can see a relay output. How to program the relay for internal temperature alarm.
A. You need to add special commands in the configurator, please see this How To page for a downloadable procedure Link